This system is one kind of pressurized water supply equipment, it has the same function with the high cistern, water towers The package system is widely used in the fields of hotels, hospitals, commercial buildings, factories and enterprises, residential quarters and other multi-story building as the perfect production and living water supply equipment. Matching with the heat exchanger unit it can also be applied to contain the impact of water s expansion, constant pressure and automatic replenishmentin the hot water closed-loop air-conditioning, heating system 1, using capsule-type air pressure tank to supply water automatically, without high cistern. It is more safe and reliable especially in air-conditioning, heating system . 2, The gas and water does not be mixxed, has not water pollution happened, to meet the requirements of water quality. 3, working with small vibration, low noise; The water hammer in the pipe network can automatically eliminated, avoiding the impact and damage to the system; operating pressure is stable and reliable. 4, To set up two pumps, operate them alternately or parallelly, to ensure the sufficient start-interval, has obvious energy-saving effect; solve the problem of suspension of water supplies because of fault from stopping work. 5, simple installation, easy maintenance, easy centralized management.
1)No need of water pool, saving both fund and energy
2)Simple installation and less used
3)Extensive purpose and strong suitable
4)Full functions and high degree in intelligence
5)Advance product and reliable quality
6)Personalized design, showing a distinctive style
Product Specification / Models
Stainless Steel No Negative Pressure Water Supply Equipment
1. Electric water supply set
2. Simple installation
4.Flow rate (T/H): 9-16
Application / Models
1)Water supply for city life
4)Prinkling & musical foudation
When the equipment is put into movement, the water from the tap-water pipe-net flows into the flow stabilizing can. When the water supply capacity of the pipe-net can meet with the demand of use, the pressure of it is kept with the normal water supply range, the negative-pressure preventing module controlled electric valve is opened and the pump moves to carry out the pressure-overlapped water supply; While the said capacity can not meet with the demand, the pipe-net pressure is lower than that for normal water supply, the said module automatically adjusts the opening of the electric valve till its being closed, at this time water supply by the flow stabilizing can is automatically switched in. The vacuum eliminator on the said can is opened therewith, preventing a negative pressure from being produced inside of the can.